0.6/1KV PVC Nyy Harga kabel 4 x 95 mm2, nyy 4 x 70 mm2 cable Applications
Because of the low voltage kabel nyy 4 x 95 mm2 and nyy 4 x 70 mm2 cable is very for laying indoors and outdoors. Able to bear certain traction during installation, but not external mechanical forces. Laying harga kabel nyy 4×16 cable in magnetic ducts is not allowed.
Harga kabel 4 x 95 mm2, nyy 4 x 70 mm2 pvc nyy cable structure
Conductor: Compact stranded copper conductor, Cl.2 as per IEC 60228 and so on.
Insulation :such as XLPE(cross-linked polyethylene) and the like rated at 90 ℃.
Sheath : PVC type ST2 to IEC 60502, black (resistance fire) and so on.
International: IEC 60502, IEC 60228 and so on.
Other standards such as BS,DIN and IECA and so on.
Packing: 500 meter/Drum of wooden or iron drum and so on.
The different expression methods of PVC/PVC Harga kabel nyy 4 x 70 mm2
Although, as a type of common power transport tool, the Harga kabel nyy 4 x 70 mm2 for fixed installation. For example, indoors, outdoors, underground, in concrete and in water. relay and instrumentation panels of power switch-gear and for purposes.The low voltage power power play an important character. So, their role is to transmit and distribute electric energy. But, the Nyy 4 x 70 mm2 has different representations in among countries. Meanwhile, in some Europe countries, people used to ask the NYY cables, NYBY cables, NYSY cables as cable 4 x 95 mm2.
The cable nyy 4×95 in difference countries
But in Southeast Asia, many person ask the non-shield conductor and insulated material is PVC cable as 600v cable. Therefore if from the perspective of application, people will call the lv power cable as low voltage underground cable. Generally speaking, if from the cable’s structure, we can call the kabel 4 x 95 mm2 as lv armoured cable or lt xlpe cable. At the same time if you are a senior cable engineer or a professional cable manufacturer. Therefore, you will according to customer’s application to define the low voltage electrical cable. So you need precise describe details specifications of the Harga kabel 4 x 95 mm2 nyy cable of hdc. Such as: the 4 core low voltage cable, 600v xlpe nyy 4×70 represent a complete cable size
Nyy Harga kabel 4x70mm fecature
Although the 4×70 Nyy harga cable only name in some countries, so little person know it, in actually it is a kinds of low voltage power cables. But in China we usually ask them YJV, YJV22, VV, VV2. At the same time, international, we named it 0.6/1kv pvc/xlpe insulation power cable. Because of, it’s conductor is copper or aluminum, core 1-5 core and so on. In addition to, this cable mainly used for some public place, such as: shipping plaza, hospital, free way, subway, and so on.
kabel nyy 4 x 95 mm2 and nyy 4 x 70 mm2 cable working
Rated voltage: 0.6/1kV
Core: 1 core, 2 core, 4 core and so on.
Max. Conductor Temp: normal (90℃), short circuit no more than 5 s (160℃ when section-area below 300mm2, 140℃ when section-area above 300mm2) and so on.
Min. Ambient Temp: such as the cable shall be pre heated if the ambient temperature is below 0℃
Min. Bending Radius: single core cable 20(d+D)±5% and so on.
Multi-core cable 15(d+D)±5%
0.6/1kv both hkabel nyy 4 x 95 mm2 and nyy 4 x 70 mm2 cable technical date
|Nom. Cross-section of conductor||mm2||4 × 70||4 × 95|
|Strands No./Dia. of Conductor||pc/mm||14/2.52||19/2.52|
|Approx. O.D.||Lower Limit (mm)||27||31|
So, if you are looking for the nyy 4×70 cable, Huadong will a good choice for you. Please contact us any time, we will rely you as soon as possible.